1. vapour recovery hose assembly
2. direct market
3. high quality
4. good service and competitive price
Hot Sale New Type Rubber Vapour Recovery Hose Assembly
At present, the fitting of vapour recovery hose assembly and the return vapour part inside nozzle are sealed in the form of dynamic seal.
Therefore, the rotation of the nozzle brought the gasoline pumped back into the fuel dispenser along the vapour pipeline, this will cause the
circulated vacuum pump scrapped and the gasoline station stopped. To the problem our company researched and developed a new type vapour
recovery hose assembly, a good solution to the above-mentioned defects, so that the vapour recovery system became much more effective,safer and greener.
1.Before installation, please check the both ends of fitting to ensure the o-ring fully equipped and good.
2.While installation, please make sure the male thread can be rotated into the end of nozzle. We recommend using the thread locker to avoid unscrewing through
3.The end which is anti-kink sleeve of vapour recovery hose assembly connected to the nozzle, and the other end connected to the break away.
2.Working pressure:not more than 16bar
3.After refueling, do not leave the vapour recovery hose assembly on the carriageway, avoid tramping, rolling and pulling.
1.Check the vapour recovery system regularly to ensure they’re in good working condition.
2.Check the vapour recovery valve and P/V valve carefully to ensure the seal performance of the vapour recovery pipeline system.
3.Check the sealing condition of connection part, if found loose or oil leakage, should be fastened with explosion-proof tool.Once failed, should be reported to the manufactory promptly.
4.Check whether the pipeline have oil smell or oil leakage, if found please contact to maintain immediately.
This Is Our Factory
Welcome to your inquiry and we would send you our best offer right away !
If you want to know more about us , welcome to visit
We can according to any standard production